|DOWNLOAD SER PDF|
|Applications||Top of Page|
May be used as service-entrance conductors and in other applications where SE cables are
permitted when installed as specified by NEC® Article 230. May be used in wet or dry locations
at temperatures up to 90°C.
|Conductors||Top of Page|
Stranded conductors: Uncoated copper per ASTM-B3, ASTM-B8, and ASTM-B787
|Phase Conductors||Top of Page|
Type THHN conductors
Black PVC (polyvinyl chloride), rated to 90°C in wet or dry locations
Jacketed with black nylon (polyamide)
One phase conductor has a red stripe on its insulation surface for easy polarity identification
|Neutral Conductor||Top of Page|
White PVC (polyvinyl chloride), rated 90°C
Jacketed with white nylon (polyamide)
|Equipment Ground Conductor||Top of Page|
Bare stranded copper conductor.
|Assembly||Top of Page|
Insulated and bare conductors are twisted together.
Glass-reinforced tape is applied over conductors.
|Jacket||Top of Page|
Gray, sunlight-resistant PVC (polyvinyl chloride) jacket over the complete assembly
|Industry Standards||Top of Page|
UL 83 (insulated conductors)
UL 854 Service Entrance Cables, File No. 11098
Federal Specification A-A-59544
NFPA70: National Electrical Code®
*It is the sole responsibility of the end user to determine suitability of this product for its intended end use and application.
|Surface Print||Top of Page|
Sample: TYPE SE CABLE STYLE R TYPE THHN OR THWN 3 CDRS 6 AWG 1 CDR 6 AWG
600V E11098-A (UL)