For use in electrical distribution circuits not exceeding 600 volts phase-to-phase. Cables may be directly buried or installed in ducts. May be used in wet or dry locations at conductor temperatures not exceeding 90°C for normal operation, 130°C for emergency overloads, and 250°C under short-circuit conditions.
- direct burial
- wet or dry locations
Hard-drawn stranded, compressed 1350 aluminum per ASTM-B230 and B901
- Black cross-linked polyethylene
- Black cross-linked polyethylene with three continuous extruded yellow stripes 120° apart
UL 854 Service Entrance Cables
Phase and neutral conductors are twisted together with a left-hand lay not greater than 60 times the outside diameter of one phase conductor.
Sample: 4/0 AWG AL XLPE 600V USE-2/YEAR