May be used as service-entrance conductors, feeders and branch circuits where SE cables are permitted when installed as specified by the National Electrical Code® (NEC). May be used only in above-ground locations; insulation rated at 90°C.
Insulated and bare conductors are twisted together then wrapped in a glass-reinforced tape. Gray, sunlight-resistant PVC jacket over the complete assembly.
- Compact stranded AA-8000 Series aluminum alloy
- Type XHHW-2 with black XLP insulation. Rated for use up to 90°C in wet or dry locations.
- A red stripe on insulation surface of one conductor.
Equipment Grounding Conductor
- Bare compact stranded AA-8000 Series aluminum alloy.
Federal Specification A-A-59544
NFPA 70 (National Electrical Code)
Sample: TYPE SE STYLE R 600V XHHW-2 AA-8000 AL 3/C 6 AWG + 1/C 6 AWG (UL) E222531 * SUNLIGHT RESISTANT *