May be used directly buried or installed in ducts in electrical distribution circuits not exceeding 600 volts phase-to-phase when installed as specified by the National Electrical Code® (NEC), and other applicable standards.
May be used in wet or dry locations at conductor temperatures not exceeding 90°C for normal operation, 130°C for emergency overloads and 250°C under
Hard-drawn stranded, compressed 1350 aluminum per ASTM-B230 and B901
Two insulated conductors
- Black cross-linked polyethylene insulation
One insulated conductor
- Black cross-linked polyethylene insulation with three continuous extruded yellow stripes 120° apart*
All three conductors are twisted together with a left-hand lay not greater than 60 times the outside diameter of one phase conductor.
UL 854 Service Entrance Cables
Sample: E302630 <AWG/kcmil(mm2)> AL TYPE USE-2 (UL) 600V XLPE SUN RES PHASE A